7. Well appears to be impacted by saline water.
8. The treatment system that has been installed appears to mitigate methane, iron, and manganese, but not addressing barium and potential concerns related to bromide.
9. It might be advisable to pull the pump - camera survey the well and seal off a portion of the well.
It appears the treatment system only reduced the level of barium to 2.85 mg/L. It may be possible that the water treatment system did not take into consideration the level of barium. A water softener may be needed. (Action- Continued Monitoring - well may be influenced by saline water- it may be possible to mitigate saline water impact - but additional work is needed.)
EPA has suggest a MCL of 0.1 mg/L. (OK) After treatment the level was 0.0015 mg/L
Total Suspended Solids - < 10 mg/L – no standard, but would recommend retesting to obtain a lower detection limit.
Add Methane (Order from us) - We can do a methane, ethane, propane - test for about $ 100.00
( self collection)-Request information .
Do you want to make a positive change in PA - that will cost you NO Money?
Help Support the Citizens Groundwater and Surfacewater Database and Submit Your Baseline Data !